AVC SET DVR is an innovating system designed to mitigate and eliminate the effect of electrical disturbances on critical industrial processes through the elimination of sags and a continuous regulation for minor disturbances.
Power generation, transport and distribution systems are limited and their problems can affect production processes as well as to produce economic consequences.
AVC SET DVR guarantees the quality of the network, meeting the demands of industrial production processes, keeping stable & constant the output voltage regardless of input voltage variations.
AVC SET DVR is a flexible voltage compensator capable of correcting variations of input voltage, to offer a highly stable voltage (± 0,5%) with immediate response (<3msec).It consists of a transformer, a reversible rectifier unit, plus an inverter. The aim of the AVC SET DVR is to offset disturbances, voltage imbalances, and to regulate them in case of possible fluctuations and overvoltages.
The system also supervises controls and logs all events. The output voltage stabilisation is assured both for balanced (all three phases) and unbalanced (some of the phases) voltage variations.
|Model||AVC SET DVR 30 kVA 60%||AVC SET DVR 60 kVA 60%||AVC SET DVR 90 kVA 60%|
|System||Master||Master + 1 slave||Master + 2 slaves|
|Nominal voltage (1) (2) (3)||208/380/400/415/480 Vac|
|Admissible voltage range (4)||+ 20% – 60%|
|Admissible frequency||50/60 Hz ±10%|
|Power||30 kW/kVA||60 kW/kVA||90 kW/kVA|
|Voltage (1) (2) (3)||208/380/400/415/480 Vac ±0.5%|
|Frequency||50/60 Hz programmable|
|Response time||< 3 msec|
|Transfer time to bypass||< 0,5 msec|
|Overload||110% during 30 seconds, 150% during 1 second|
|THREE-PHASE CORRECTION CAPABILITY (4)|
|Range for continuous regulation||+ 20% – 25% Vnom|
|Maximum sag without voltage alteration||60% Vnom, up to 30 seconds in duration|
|Maximum sag without switching to bypass||70% Vnom, up to 1 second in duration (5)|
|Dielectric rigidity||2,5 kV – 1 minute|
|Communications||Standard: Web HTTP, SNMP, ModBus; Optional: modem or router|
|Control panel||Display, keyboard and leds|
|Protections||Short-circuits, current limitation, overload, RFI filter, required disconnections|
|Maintenance switch||Only Master system: optional ; Parallel system: Yes|
|Directives UNE-EN 50178 (98), EN 61000-6-2, EN 61000-6-3||UNE-EN 50178 (98), EN 61000-6-2, EN 61000-6-3|
|DIMMENSIONS AND WEIGHTS (2)|
|Dimensions (high x wide x depth)||1495x653x703 mm||2095x1306x703 mm||2095x1959x703 mm|
|Weight||330 kg||760 kg||1140 kg|
|MANUAL BYPASS CABINET (2)|
|Dimensions (high x wide x depth)||700x653x703 mm||–||–|
|MODEL||POWER||MAXIMUM VALUE FOR CONTINUOS REGULATION||MAXIMUM SAG WITHOUT VOLTAGE ALTERATION||MAXIMUM SAG WITHOUT SWITCHING TO BYPASS*|
|AVC SET DVR 30kVA 60%||30kVA||+20% -25%||60%||70%|
|AVC SET DVR 60kVA 60%||60kVA||+20% -25%||60%||70%|
|AVC SET DVR 90kVA 60%||90kVA||+20% -25%||60%||70%|
|* Depending on AC input breaker protection and AC network impedance|